I’m a little annoyed with having to deal with air conditioning nonsense right before a weekend I don’t get any time off from work because we’re so understaffed. We have an HVAC contractor who is supposed to deal with this but they’re completely clueless when it comes to large systems. They have one guy in the company who understands the Metasys controls and somehow I know more about them than he does.
The last big issue I had was with this one air handler / fan coil unit on the roof that cools both control rooms and our newsroom via a Medusa head of VAV boxes. First it had been shutting down, it turned out the variable frequency drive was on an HVDC overvolt fault and didn’t automatically restart. I programmed it to do so. The service company looked at me like I was speaking Martian COBOL when I explained this to them.
I also asked them if the belts to that blower it runs were too loose. They don’t know. They couldn’t advise me on this and didn’t know how to check. I’m not touching this with a social distancing pole.
Today it was acting up in a different way and I found Metasys reporting the cold duct pressure was 0.1″ water column. When I opened the blower access door on this totally turdly air handler, it jumped up to 0.7″ and the VAV boxes actually started, you know…… working. Opening the door took an unreasonable amount of force and only after I opened the door, the system started calling for less than 100% blower speed. Hmmmm.
Gee I wonder why there’d be that much airflow restriction on the inlet? Let’s see, shall we?
These coils were supposedly cleaned! Uh…. No.
On a side note, the fact that our chiller’s variable output capability is simply not used and instead it was just saddled with this foam rubber covered Chipotle burrito tank and set to on/off cycle makes me wonder
Here’s to hoping this hot weekend goes uneventfully.